Industrial Accident: a boiler fueled by both oil and natural gas exploded while being lighted after switching fuel sources. The burner management was incuded in an existing Distributed Control System DCS that controlled the oil gun purge, firebox purge, and ignition sequence. The DCS programming from a prior project was not properly modified to accomodate the particular requirements of this complex dual fuel system. The altered code affected the oil gun steam purge timing during repeated switchover attempts.
Additional information on boiler/burner-related engagements can be found here.
Copyright © 2017 Arthur Zatarain, all rights reserved. Some images are modified for confidentiality
or illustration clarity. This site should not be used as a technical or legal reference.